|Flashing frequency||Steady burning|
|Light source||Red LED|
|Beam angle||360° horizontal beam angle|
|≥10° vertical beam spread|
|Method of synchronization||Same power supply voltage signal mode|
|Lightning protection level||10KA|
Widely used in various fields of the Air Force, civilian airports and obstacle free airspace, helipads, iron tower, chimney, ports, wind power plants, bridge and city high-rise buildings where require aviation warning.
Usually used below 45m
● 1. Lamp shade of the light adopts PC with anti-UV which is high efficiency light transmission up to 90%, quite high impact resistance and fit the bad environment very well.
● 2. House of the light is made of aluminum alloy and steel, painted by spraying plastic, the structure is high strength ,resistance to corrosion
● 3. Using Parabolic reflector optical design, range further
● 4. Light source adopts LED with long life-span ,lower power consumption and high efficiency
● 5. Based on the single chip computer control , automatic identification sync signal ,do not distinguish the main light and auxiliary light ,and also could be controlled by controller
● 6. Same power supply voltage with synchronous signal , integrate in power supply cable ,eliminate the damage by error installation caused
● 7. Used the photosensitive probe fit for the natural light spectrum curve, automatic control light intensity level.
● 8. The circuit of the light has surge protection whose lightning proof ability is In 7.5KA/5 times, Imax 15KA so that the light is suitable to harsh environment
● 9. Integral structure, protection lever of IP65.
● 10. Synchronizing function is available
CK-11L Low intensity LED Obstruction Light Type B installation instruction
Installed the light on horizontal surface that have enough strength.
（1）Installed the light on horizontal surface that have enough strength.
（2）The power supply of this type of light is AC220V. Do not use other power supply. Otherwise the light will be quickly damaged.
（3）The identification of the line, lamps with one four-core cable:the brown wire connect to the Live line, black wire connect to Null wire, the yellow-green wire is the ground wire. Blue is signal line.
● All the lines must be connected correctly, otherwise may damage the light. Please look at the mark and introduction carefully.
● Besides, in order to avoid being struck by lightning, the lamp is prohibited to install on the top or the edge of the iron tower (When necessary, it could add lightning arrester on the outside of the lamps).
● it is normal situation there will be a temperature rise when the lamps working.
● When the light working, in order to avoid the dangerous, please don’t open any part of the light body.
● non-professional workers do not disassemble , once discovered ,shall not guarantee.